Conductive Static Dissipative Flooring ESD Anti Static Vinyl Floor
Technical Data for Anti Static ESD vinyl floor tile:
Anti Static Vinyl(PVC) Tile
Amount of anti-wear (SJ/T11236-2001) <0.02g/sqm 1000r
Anti-wear Properties EN660PT2
Residual Concavity EN443/DIN51955
ESD Anti-static Vinyl floor tile construction norm:
1.1 General provisions
1.1.1 Antistatic polyvinyl chloride (PVC) including construction of
the ground dealing with the grass-roots level, grounding systems,
glue preparation, anti-static polyvinyl chloride (PVC) Tiemianban
(hereinafter) of the pave and stick and cleaning Tiemianban
construction, testing, and quality inspection.
1.1.2 Construction site, the temperature should be between 10-35 ℃
relative temperature not more than 80%; ventilation should be good.
Indoor other construction projects should have been basically
1.2 Materials, equipment and tools
1.2.1 Construction materials should comply with the following
1 Tiemianban: physical properties of size and appearance should be
consistent with the "anti-static Tiemianban general specification"
SJ/T11236 requirements, and a permanent anti-static properties. Its
size and surface resistivity: I. Type Tiemianban electrostatic
resistance values should be less than 1.0 × 106 Ω, static
dissipative panel of medical treatment in the resistance values of
1.0 × × 109 Ω 106-1.0.
2 Conductive adhesive: should be non-water-soluble glue, Tiemianban
resistance value should be less than the resistance value, bond
strength should be larger than 3 × 106N/M2
3 Plastic electrode: Uniform color should be used, the same
diameter, flexible material good.
4 Conductive copper foil for the network: thickness shall be not
less than 0.025 mm, width to 15 mm.
1.2.2 Tiemianban ventilation should be stored in dry storage, away
from the acid, alkali and other corrosive substances. Handling
should be Qingzhuang light dumping, is prohibited uncompromised
impact. Outdoor prohibited under the sun and the rain.
1.2.3 Commonly used construction equipment (including tools) should
include slotting machine, plastic gun, rubber hammer, cutting
knife, ruler, brushes, waxing machine, with its specifications,
performance and technical indicators should be consistent with
requirements of the construction process.
1.3 Preparations for the
Figure 1.3.1 familiar with the design, construction and inspection
of the scene.
1.3.2 Construction of the development programme, drawing
anti-static grounding system ground plans, grounding terminal map
and grid layout.
1.3.3 Requirements under construction technology available in
various construction materials, equipment, tools, and placed
1.3.4 Surface area of more than 140 m2, in a formal demonstration
should be done before construction of laying.
1.3.5 Construction site should comply with the following
A grassroots ground-ground cement or terrazzo floor when:
1) Ground should be clean and should be on the ground in the paint,
adhesives and other remnants of clean up.
2) The ground should be formed by two meters ruler checks gap
should be less than 2 mm. If there are cracks or uneven areas need
to be filled.
3) the ground should be dry, if the underlying ground water should
be dealt with.
4) Can not afford to hard surface should be sand, mortar strength
should not be lower than No. 75.
2 Grassroots ground-floor (wood floors, ceramic tile, plastic,
etc.) should be removed original flooring, and on the ground should
be thoroughly remove the residue of glue.
3 Construction site should be equipped with artificial lighting
1.3.6 Determine Grounding Terminal Location: 100 m2 in area within
the grounding terminal should not be less than one; each additional
area of 100 m2, should additional grounding terminal 1-2.
1.3.7 Construction thoroughly before cleaning the grass-roots level
ground, the ground may not be left drosses, dust, and other milk.
1.4.1 Designated baseline, depending on the geometry room
1.4.2 Should be laying the network layout of conductive copper
mesh. The vertical and horizontal cross-copper, should be placed at
the centre of Tiemianban. The roll-out of the copper should be
straight, not curly, nor intermittent. Terminal connection with the
grounding of the copper foil should allow sufficient length.
1.4.3 Configuration conductive adhesive: carbon black and glue
weight ratio should be 1:1 configuration, and stir evenly.
1.4.4 Shuajiao: At the difference on the ground, has to pave and
stick conductive copper above, coating should be uniform,
comprehensive, and after natural coating dries.
1.4.5 Pave and stick Tiemianban: dehydration to be coated with
non-stick on the ground to dry hands, we should start to pave and
stick production. Tiemianban pave and stick will be the two right
angle at the baseline side, should pave and stick rapid fast. board
and board should be left between 1-2 mm gap, the gap width should
remain basically the same. rubber hammer uniform Hitting board, and
at the pave and stick-checks to ensure that the firm paste. edge of
the application of non-standard ground Tiemianban pave and stick
filled, non-standard Tiemianban Tiemianban standards used by the
cutting knife from cutting.
1.4.6 Pawnshops terminal affixed to the ground, should be the first
to connect grounding terminal leads impregnable fortress chaff, or
using soldering methods and Crimp solid grounding terminal links.
Continue to pave and stick panel.
1.4.7 After the entire room to pave and stick should be used along
the seams Tiemianban grooving a welding machine slot. Slot-line
should be straight and uniform, trough 3 ± 0.2mm suitable.
1.4.8 Application plastic welding torch in the slot for
thermoplastic welding, plate and the plate connecting. Welding
Application of excess-profits knife cuts, but not Tiemianban
scratches the surface.
1.4.9 Grounding system construction should include Conductive
Adhesive Layer, conductive copper grid, grounding copper, grounding
terminal, grounding Yinxiaxian, grounding devices, and so forth. In
addition to provisions of this chapter, the remaining provisions
shall be consistent with this standard.
1.4.10 Pave and stick work completed, clean the ground, and
anti-static coating of wax should be protected.
4.5 Test and quality examination
4.5.1 Antistatic polyvinyl chloride (PVC) Ground detection devices
should be standardized with the "common detection apparatus" with
4.5.2 Test environment: the temperature should be between 15-30 ℃
relative to the temperature is less than 70%.
4.5.3 Antistatic polyvinyl chloride (PVC) ground surface
resistivity values and value systems resistance measurement methods
should be adopted following:
1 Surface resistivity measurements: the whole anti-static ground
should be split into 2-4 m2, surveying the region, randomly
selected 30% -50% of the survey region, the two electrodes were
placed Tiemianban surface, a distance of 900 mm, with the electrode
Tiemianban contacts should be good. At the same from the 2-4 m2 in
the region should be measured numerical 4-8 months, and recorded.
2 Resistivity measurement system: from the ground in the recent
regional terminal randomly selected number of points should be a
good surface electrode and Tiemianban contacts, and the other
electrode and grounding terminal linked to resistance values
measured systems, and for record .
3 Quality assessment method should be "Dipi count sampling
inspection procedures and sampling table" GB2828 regulations.
4.5.4 Electrical Performance indicators should meet the following
1 Requires a derivative of the electrostatic type, surface
resistivity and system resistance values of less than 1 × 106 Ω.
2 Requires a static-dissipative, and the surface resistance and
resistance values in the system 106-1 × 1 × 109 Ω between.
3 system grounding resistance value should meet the design
1.5.5 Presentation performance should meet the following
1 May be hollowing, delamination, cracking;
2 No obvious rugged;
3 No obvious scratches;
4 No obvious color.
1.5.6 Nndertake anti-static polyvinyl chloride (PVC) testing ground
units should be authorized by the State with appropriate aptitude
test reports as the authoritative body.